Overview of Bacnet/IP implementation
Our Bacnet vendor ID is 571
Converter supports full segmentation.
Supported properties can be displayed by clicking on objects.
Properties support depends on their implementation in communication drivers. All basic properties are implemented.
Not implemented properties will always return null or 0.
Changes to Bacnet/IP standard
Who has, Who is, I am, I have and COV are not using broadcast
Communication is not binded only on one port, responses are sent on senders port.
These basic parameters are available:
Name of Device object
Instance of Device object
Port number in hexadecimal format
Broadcast mask - at initialization is once used to sent I am command, then will be used only for Bacnet browser
Enables BACnet/IP Broadcast Management Device service.
In the right side of the screen is located Broadcast Distribution Table.
Local Bacnet points
Displays list of local points with their states.
Value of the point can be changed by selecting and then right-clicking desired row, context menu for value change should pop up.
Changed value will be written to connected device only if active driver supports such action.
Exports Bacnet EDE