Bacnet/IP Reading and writing of remote points
Allows reading of points from external Bacnet/IP device and their writing into local points. Local points can be later written to points of external Bacnet/IP device.
First column is used to select rows for deletion or bulk editing.
Double-clicking row will open editor
Point instance check - sents Who has command with points name. Configuration will be updated if point has changed.
Automatic point instance check interval
Local point - local point name for read and write
Local point itegrity - indicates if local point exists
Function - off/reading COV/writing pool/write out of service/write Present value(via priority array)
Pool time in seconds / COV interval length / writing at local point change
Priority - priority for writing to priority array
Opens Bacnet/IP browser
Add Bacnet/IP device manualy
Read point from selected device
Sends Who is broadcast
From list you can select points you wish to add. Selection will be confirmed by pressing OK button.
When you create point manually, you are able to create bridge between drivers i.e. M-Bus point will be able to write to Excel
Displays current state of read and write operations for points.
Enables subscription to broadcasts from external Bacnet/IP device